INVESTIGATION OF THE EFFICIENCY OF OPERATION OF A CENTRAL TYPE INVERTER AT AN INDUSTRIAL SOLAR POWER PLANT
When calculating a solar power plant, the efficiency of the inverters is taken in accordance with the efficiency curve provided by the manufacturer. This calculation is usually done in PV Syst software. The inverter manufacturer provides a special file that contains all the inverter specifications. This article examines the inverter's performance under real-world operating conditions. With the entry into force of the Law on the Electricity Market, the owners of industrial SES must submit a forecast of SES operation. The development of the forecasting model uses the efficiency of all components of the SES. As in the real world, the performance is different from that stated by the manufacture, the accuracy of the forecast is reduced. Therefore, before starting the development of the model of forecasting of the SES, it is necessary to examine the efficiency of all its components. One of the main components of the SES is the inverter. The efficiency of its operation depends on the following factors: voltage on solar panels, current from the PV, voltage in the power supply network, cooling system, and the internal design of the inverter. In this work, FES is selected where all inverters have the same number of solar panel configurations.
During the study, the minute data of the operation of each inverter for the period September 2018 to June 2019. Were processed. In the future, the data from the study will be used to predict the operation of this FES. Ref. 10, fig. 6.
2. DSTU 8635:2016. Ploshchadky dlya fotoelektrychnykh stantsiy pryyednannya stantsiy do elektroenerhetychnoyi systemy. [DSTU 8635: 2016 "Surfaces for photoelectric stations connection of stations to the electrical energy system"]. [Electronic resource]. URL: http://eom.com.ua/index.php?action=downloads;sa=downfile&id=3656. [in Ukrainian].
3. Reactive Power Interconnection Requirements for PV and Wind Plants–Recommendations to NERC. [Електронний ресурс]. URL: https://prod-ng.sandia.gov/techlib-noauth/access-control.cgi/2012/121098.pdf. [in English].
4. Brown T. Transmission network loading in Europe with high shares of renewables. IET Renewable Power Genera-tion. 2015. vol. 9. no. 1. Pp. 57-65. [in English].
5. GB/T19964-2012. Photovoltaic power plant power system access technical requirements. Beijing: General Admin-istration of Quality Supervision, Inspection and Quarantine of People's Republic of China. China National Standardization Man-agement Committee. 2012. [in English].
6. Campbell M., Aschenbrenner P., Blunden J., Smeloff E., Wright S. The drivers of the levelized cost of electricity for utility-scale photovoltaics. SunPower Corp. 200. [in English].
7. Zhou J., Gole A. VSC transmission limitations im-posed by AC system strength and AC impedance characteristics. Proc. 10th IET International Conference on AC and DC Power Transmission (ACDC). 2012. Pp. 1-6. [in English].
8. Collins L., Ward J. Real and reactive power con-trol of distributed PV inverters for overvoltage prevention and increased renewable generation hosting capacity. Renewable En-ergy. 2015. vol. 81. Pp. 464-471. [in English].
9. Utility-scale solar photovoltaic power pants-A pro-ject developers guide. International Finance Corporation (IFC). 2015.
10. Molina-Garcia A., Mastromauro R.A., Garcia-Sanchez T., Pugliese S., Liserre M., Stasi S. Reactive power flow control for PV inverters voltage support in LV distribution net-works. IEEE Trans. Smart Grid.
Abstract views: 21 PDF Downloads: 10